|Place of Origin:||Baiyun,Guangzhou,Guangdong,China|
|Certification:||CE Approval / Test Reports / Patent Right|
|Minimum Order Quantity:||Negotiable|
|Price:||Negotiable if good quantity|
|Packaging Details:||230x230x450mm colorful box/pc, and 4 pcs in 490x500x500mm carton|
|Delivery Time:||Around 6 working days upon receipt of order payment|
|Payment Terms:||100% TT / LC / Western Union / MoneyGram / WeChat Transfer / Alipay / Wanda Money Transfer / Cash ahead|
|Supply Ability:||1000 pcs/month|
|Patent Status:||Owned & Normal||Delta T:||60μs In Advance|
|Metal Housing:||304 Stainless Steel||Iimp Withstanding:||≥ 200kA|
|Test Standards:||UNE 21.186:2011 Paragraph C||Testable Or Not:||Yes|
|Approx Weight:||4,000g||HS Code For Lightning Conductor:||8535400000|
Oversea tested early streamer emission types of lightning conductors on building
|SMT-ESE60 ESE Types of lightning conductors Operation Principles|
|Detection of download leader||Continuous measuring of electric field gradient (ΔE/Δt)|
|Upward streamer development conditions||TSTLP®-SMART Technology optimizing the streamer development conditions|
|Upward streamer emission||Sparking by High Voltage Impulses|
|Internal circuits||6 Independent working unit|
|Central rod||Full electrical continuity|
|Enclosure Material||Superior Stainless Steel|
|On-site testing capabilities||Proprietary E.S.E. types of lightning conductors tester|
Max Radius Protection of SMT-ESE60 early streamer emission lightning conductor :
Level 1: 80m radius protection.
Level 2: 90m radius protection.
Level 3: 105m radius protection.
Level 4: 120m radius protection.
MP4 FLASH of TSTLP ESE Type of Lightning Conductor VS Ordinal Conductor ZONE of PROTECTION, check/download @ https://drive.google.com/file/d/1oluGnqguWksS9eEWPnKvk4PTSCxHQQkh/view?usp=sharing
Additional protection against direct lightning strike for the highest 20% of the structure height for buildings greater than 60 m or any point above 120 m, using ese types of lightning conductor or any other means must be implemented at each façade wall according to a valid standard. Furthermore a minimum of 4 Down conductors, interconnected by a ring conductor when applicable, shall be used, distributed along the perimeter and if possible at each angle of the building.
NOTE: in general the risk due to the lateral flashes is low because only a few percent of all flashes to tall structures will be to the side and moreover their parameters are a lot lower than those of flashes to the top of structures.
Download TSTLP ESE Lightniing Conductor pdf Catalog @ https://drive.google.com/file/d/1sHzPnbVjZLkIAeXGNRp4bKSoYsNoqf1C/view?usp=sharing
Tag: types of lightning conductors, lightning conductors on building
Contact Person: Franklin